The slim low-static, low profile ducted indoor units, can in many instances be fitted in between joists to create higher ceiling for dramatic affect.
Auto changeover (Heat Recovery only)
Dual thermistor control
Soft dry (dehumidification)
Fan speed control
|Cooling Mode Performance|
|Power Input1 W)||85|
|Heating Mode Performance|
|Power Input1 W)||85|
|Sound Pressure3 B(A) (H/M/L)||33 / 32 / 29|
|Net Unit Weight (lbs.)||46.3|
|Communication Cable4 No. x AWG)||2 x 18|
|Airflow Rate H/M/L (CFM) Standard Mode||283 / 229 / 194|
|Airflow Rate H/M/L (CFM) High Mode (Factory Set)||283 / 229 / 194|
|External Static Pressure (in. wg) Standard Mode||0|
|External Static Pressure (in. wg) High Mode (Factory Set)||0.08|
|Power Supply (V/Hz/ø)||208-230 / 60 / 1|
Power wiring is field supplied and must comply with the applicable local and national codes.
This data is rated 0 ft above sea level, with 25 ft of refrigerant line per indoor unit and a 0 ft level
difference between outdoor and indoor units. All capacities are net with a combination ratio between
Cooling capacity rating obtained with air entering the indoor coil at 80ºF dry bulb (DB) and 67ºF wet
bulb (WB) and outdoor ambient conditions of 95ºF dry bulb (DB).
Heating capacity rating obtained with air entering the indoor unit at 70ºF dry bulb (DB) and outdoor
ambient conditions of 47ºF dry bulb (DB) and 43ºF wet bulb (WB).
1Power Input is rated at high speed.
2Take appropriate actions at the end of HVAC equipment life to recover, recycle, reclaim or destroy
R410A refrigerant according to applicable regulations (40 CFR Part 82, Subpart F) under section 608
3Sound Pressure levels are tested in an anechoic chamber under ISO Standard 3745.
4All communication cable to be minimum 18 AWG, 2-conductor, stranded, shielded and must comply
with applicable and national code. Ensure the communication cable is properly grounded at the master
outdoor unit only. Do not ground the ODU-IDU communication cable at any other point.
|Download||Type||Category||Product Name||Model No.|
|Submittals||Indoor Units - Ducted||Ceiling-concealed Low Static Built-in||ARNU073B3G4|
|Engineering Manuals||Indoor Units||All Products||NA|
|Engineering Manuals||Indoor Units - Ducted||Ceiling Concealed High Static, Low Static, Low Static Built-In & Vertical/Horizontal Air Handlers||NA|
|BIM / REVIT||Indoor Units||NA|
|Product Warranty||Warranty Card 2/7||Multi V™ IV, Water IV, Space II, Indoor Units, DOAS & ERV||NA|